What is Temperature Qualification
This article will touch base with the general concept of qualification for equipment used to store temperature sensitive assets such as medicine, blood samples, DNA etc.
Download one of our sample Qualification protocols here
- Fridge in a pharmacy
- Freezer in a pharma company
Why is it important to get Temperature Qualification?
Temperature Qualification is done on equipment used for temperature-critical applications, such as fridges, freezers, incubators and cold rooms. A Qualification is a key process before goods can be stored. By qualifying and certifying your equipment you are ensured that during normal operating conditions it is always capable of maintaining the specified critical values throughout the entire temperature interval. Additionally, the test and certification allows for a better understanding of the performance of both the equipment and the enclosed area. Depending on the type and use case of the equipment, there can also be a need for testing other environmental parameters, but as temperature is the most prevalent one, this is what the article will focus on.
How is a Mapping study different from a Qualification?
Mapping and Qualification are not the same things, but a mapping study is often a part of a qualification. Both are processes that need to take place typically before goods can be stored. However, whereas mapping solely focuses on analysing the uniformity of the distribution of temperature, a qualification procedure extends beyond this. Within a qualification procedure all relevant equipment is verified and tested so that it can be ensured that everything is installed and operated correctly. The procedure also tests the equipment’s capability of achieving the desired temperature. This means that if a storage room is qualified for 0-5 degrees Celsius, both the room and the associated equipment are capable of maintaining the temperature within that exact interval.
What equipment and assets require Temperature qualification?
The following are some of the equipment that traditionally requires temperature qualification and some of common use-cases for each.
- Refrigerators used for storing medicines or vaccines
- Freezers -18° C (0° F) for keeping frozen food, vaccines, certain medicine etc.
- Ultra Low Temperature (ULT) freezer −40 to −86 °C (−40 to −123 °F) used for storing. the Covid-19 vaccine from Pfizer-BioNTech e.g.
- Cold rooms for storing consumer goods and foods etc.
- Vans and trucks used for local distribution of medicine.
- Incubators for growing bacteria cultures e.g.
- Insulated Boxes used for storing medicine for short durations under controlled temperatures.
- Cryo Freezers for long-term storage
- Refrigerated containers (reefers) for long distance transport of medicine
- Thermal Insulated Containers with or without auxiliary power for storing medicine
- Stability and Humidity Chambers
- Cleanrooms used for manufacturing electronics, pharmaceutical products, and medical equipment etc.
What are the steps in a Temperature Qualification process?
The process of qualifying a piece of equipment follows the V-model, and consists of different types of tests that verifies and documents the design specifications for each. The tests have to be carried out in accordance with protocol and for each type of equipment separately. The entire process explained can be seen below.
- User Requirement Specification (URS)
URS is the first document required. Here the users requirements for the equipment are documented. This could be a specific temperature interval for a fridge.
- Risk analysis
To mitigate risks, a thorough assessment of what can go wrong is made. Risks are evaluated and ordered in respect to probability, severity and detectability.
- Design Specification/ Qualification
Specification of the equipment that needs to be acquired. What model, type, size, manufacturer etc.
- Installation Qualification
Here it is checked whether the right equipment has been purchased, that all components are calibrated periodically, installed according to the specifications, and maintained and operated in accordance to the guidelines of the manufacturer.
- Operational Qualification – Mapping
Operational Qualification is the first part of the mapping process, and here the equipment’s ability to function and correctly maintain a specific temperature is tested. The first test is a “dry run” before the equipment is put into service.
- Performance Qualification – Mapping
Lastly, the Performance Qualification Mapping is made to test whether the regulations work when operating with full capacity, and under all types of conditions.This allows for full reliability and ensures correct performance no matter the distribution nor material of the equipment.Click here to read more about about how a Eupry mapping is conducted.
What is a typical protocol for Temperature Qualification?
Having gone through all the steps in the V-model, and successfully completed and verified all tests, the asset/ equipment is deemed certified in all respects. Only if any deviations arise during some of the processes, must they be rectified and retested before the process of qualifying the equipment is completed. However, the scope of the retesting depends on the severity of the deviations observed.
Can Temperature Qualification be done real-time?
When getting a Eupry Temperature Calibration the entire procedure is done using our WiFi data loggers. With these the data is transmitted real-time to our website, from where you can track every procedure and test conducted in each step of the qualification. Thereby, you are given full transparency of the process and provided the ability to mitigate the risk of time loss, as deviations can be handled immediately, thus avoiding having to retest.